产品详情 彩53彩票网 > Power Station Check Valve > H48Y Air Exhaust Check Valve Product Details
H48Y air exhaust check valve
Follow times: Release time: 2014-11-27
The air exhaust check valve is installed on the high-pressure feed pump outlet pipe of the thermal power unit to prevent the feed water from flowing backward and protect the feed water pump. This valve works with the pump's minimum flow automatic recirculation bypass valve. When the feed pump is at low load or the outlet shut-off is closed, the automatic recirculation bypass valve should be in the open position to ensure the safe operation of the pump. When the air check valve is opened, the recirculation bypass valve is automatically closed. Not suitable for medium containing solid particles and high viscosity.
As a principle: Open the outlet valve, the feed pump starts, and after the feed water reaches a certain pressure, the valve flap rises to a certain height under the action of the feed water pressure, pushes away from the valve seat, and the feed water flows out. At the same time, due to the rise of the valve flap, the connecting rod is driven to rotate, and the valve sheet of the drain port is turned, so that the recirculating blade valve is moved downward and the drain port is closed. When the feed water flow rate decreases, the valve flap drops, pushing the connecting rod to open the drain valve disc, and opening the recirculation door to maintain the minimum allowable flow of the pump. When the pump is stopped, the valve flap automatically drops and closes the valve port channel to prevent damage to the high-pressure water hammer water supply system.
Structural features: The valve works with the recirculation bypass valve to maintain the safe operation of the system. The main valve flap moves up and down. When the medium flows backward, the channel is closed under the action of the medium pressure and the spring. At this time, the bypass valve opens. When the main valve flap is fully open, the bypass valve closes. The clapper seal is made of stainless steel surfacing, which is wear-resistant, scratch-resistant and reliable. · The valve should be installed vertically.
Material of main parts
Valve body, connection flange, exhaust flange, flange cover
Carbon cast steel
Guide shaft, fork, shaft sleeve, slider, exhaust sleeve, exhaust tray
Disc, disc body, disc shaft, connecting fork
High-quality carbon steel
Cast aluminum bronze
Bolts and nuts
High-quality carbon steel
(kg) Weight (kg)
The working principle of the air check valve is as follows:
Open the outlet valve and start the feed pump. After the feed water reaches a certain pressure, the valve core will automatically rise and push away from the valve seat, and the feed water will flow out. At the same time, the spool link pulls the vent valve
Sheet closes the vent. When the feedwater pump flow rate is reduced, the valve core drops, pushing the connecting rod to pull out the drain valve plate, and open the recirculation door to maintain the minimum flow rate of the pump. When the pump is stopped,
The valve core automatically drops to close the passage, thereby preventing the high-pressure water hammer from damaging the water supply system.